|Place of Origin:||China|
|Model Number:||BR275-60 1P|
|Minimum Order Quantity:||100 Piece/Pieces|
|Packaging Details:||EXPORT PACKING|
|Delivery Time:||Shipped in 15 days after payment|
|Payment Terms:||L/C, D/A, T/T, Western Union|
|Supply Ability:||50000 Piece/Pieces Month|
|Item Name:||Surge Protection Device||Keyword:||AC SPD|
|Circumstances Temp:||-40℃-80℃||Protective Level:||IP20|
|Pole Number:||1P||Type:||Type 2 Class C|
IP20 Type 2 Surge Protection Device,
UL94-V0 dc spd type 2,
UL94-V0 Type 2 Surge Protection Device
Single Pole IP20 Electric Type 2 Class C Surge Protection Device
2) Status indicator: Green-OK, Red-Failed.
3) Working temperature: -40°C-80°C; Relative humidity: 5%-95%
4) Housing protection level (IEC 60529): IP20
5) Housing material fram-retarded level (Ul94): UL94-V0
BRITEC Type 2 Class C Surge Protection Parameters:
|Model Name||BR275-60 1P|
|Product Type||Surge Protection Device|
|SPD dassification according to EN61643-11||Type 2|
|SPD dassification according to IEC61643-11||Class II|
|Max. Continuous Voltage Uc||275V|
|Max. discharge current (8/20µs) Imax||60kA|
|Norminal discharge current (8/20µs) In||30kA|
|Voltage protection level Up||≤1.5kV|
|Max. backup fuse||200A gG|
|Response time tA||≤25ns|
|For mounting on||35mm Din rail|
|Degree of protection||IP20|
|Manufacturer Guarantee||2 Years Guarantee|
|No. of Phases||Single-Phase|
|Number of Poles||one pole|
|Operation temperature range||-40 ~ +80 degree|
|Remote control contacts||Optional|
BRITEC Type 2 Class C Surge Protection Application:
BR275-60 1P is designed according to the IEC and GB standards, it enables the connection between the power supply system and an equipotential network instantanceously when the surge occurs and limit the residual voltage to a certian level to protect the devices protected. BR275-60 1P is used for Single phase TN systems.
BRITEC Type 2 Class C Surge Protection Product installation:
1. SPD apply to power distribution system 275V second-level lightning protection, it is installed in parallel on into the line side of the total power distribution equipment or the power distribution box in the buildings, with 35mm electrical lead rail, Kevin connections can be used. Cut off the power before installation, strictly prohibit powered operation.
2. Before installation please according to installation diagram of connections, including L1, L2, L3 all are the phase line, N is zero line, PE is ground line, please connect correctly. When installation is complete, close the automatic circuit breaker, check the working condition is normal or not.
3. During using lightning protection module, we should monitored and check the status display window regularly, when the display window was red or remote terminal output signal ,it means the lightning protection module failure, it should be promptly repaired or replaced.
4. Apply to indoor operation, such as outdoors installation, you must install waterproof shell.
5. All wirings must be solid and connected by electric.
6. Lightningproof grounding should be consistent with lightning protection regulatory requirements, grounding wire should be as thick and short as possible.
Wenzhou Britec Electronic Co., Ltd. is a professional engaged in SPD products research and development, design, production and service in the integration of modern professional surge protection production enterprises, production base is located in Yueqing, Zhejiang, China. With OEM/ODM high standard production workshop, has a new standard of high-end production equipment, perfect supporting factory layout is reasonable, the spacious production workshop, according to the international surge protector factory standard production design, is the domestic strong r & d manufacturers.
Q1: What is the MOQ of each item?
A: Usually the MOQ is 100 pcs. If this product we have in stock, there is no limitation for MOQ.
Q2: Do you have any guarantee for products?
A: Yes, sure. All products have two years guarantee.
Q3: Are you a factory or a trading company?
A: We are a factory with trading lines. We have in SPD field for more than 17 yeas. We have full experience of producing surge protection device.
Q4: How to control the quality?
A: Each product must be test before shipment. Our production line full with professional skills and strict stardars.
Q5: How long does it take to delivery?
A: If have stock, within 1 week we can finished all the delivery. If no have stock, normally around 3 weeks, depends on order.
Contact Person: Xu